When the work is completely ready for inspection and a twenty-four (24) hour notice is given for such inspection. The approved set of drawings must also
be on the job site.
Depending on the type of construction, you could have the following: footer, slab, crawl, rough building, rough electric, electric trench, insulation,
fireplace, temporary pole, electrical service release, interior gas line, sump pump connection, ceiling, walls, final building, final electrical, fire
suppression testing, final zoning.
Thirty (30) inches below grade.
Twenty-four (24) inches to the top of the cable. Twenty-six (26) inches to the bottom of the cable. Red electrical caution tape to be secured to side
of trench twelve (12) inches above the wire.
Twenty-four (24) inches. The cable shall be protected in pipe (PVC or rigid).
Minimum width: 20". Minimum height: 24". Sill height: 44" maximum above floor; 5.0 s.f. clear opening (main floor); 5.7 s.f. clear open (upper floor) and basement.
Yes. .006 polyethylene.
Yes, just before dry walling.